Max Water XLP-4040 2300 GPD Commercial RO Membrane
The best Membrane type to filter the MAPLE SAP allows for a greater flow but can pass small amounts of sugar as concentration increases. Check this PDF file for more detail about A Sap to Syrup Guide.
It is applicable to the desalination of municipal water, groundwater with salt concentration less than 1000ppm. It can be widely used in pure water preparation and related industries.
|Model||Active Membrane Area ft2(m2)||Permeate Flow GPD(T/D)||Stable Rejection Rate (%)|
|Concentration of Solution (NaCl)||Temperature(?)||pH Value >||Operating Pressure psi(MPa)||Recovery Rate(%)|
Notes: The permeate flow of a single membrane element may vary within ±15%.
Operating Limits and Conditions of Membrane Element:
|Max.Working Pressure||600 psi(4.14MPa)|
|Max. FeedWater Temperature||45 ?|
|Max. Feed Water Flow||3.6m3/h|
|Free Chlorine Concentration of FeedWater||0.1mg/L|
|pHRange of FeedWaterDuring Continuous Operation||2-11|
|pHRange of FeedWaterDuring Chemical Cleaning||1-13|
|Max. Pressure Drop of Single Membrane Element||15psi(0.1Mpa)|